Manufacturer: Legacy Chiller Systems
Condition: Used. Used with normal signs of use. Exterior cabinet is weathered and tag is unreadable on that cabinet. The photos show the exact item(s) the buyer will receive.
Notes: This is a split system: The indoor cabinet contains the compressor, pumps, evaporator/heat exchanger, 80 gallon tank, and controller. The outdoor cabinet contains the condenser coil, contactor, and fan.
We ran this system with a full tank of water. According to our calculations, the cooling capacity at room temperature was more than 5 tons. The system is rated at 5 tons. A qualified refrigeration tech assembled the system, added R-22, replaced a contactor, installed fuses, removed a previous user's wiring, and checked the system for proper operation. The filter/drier was replaced and the system was evacuated for several days to assure good vacuum before refrigerant was added. A micron gauge was used.
The system has been assembled on a pallet for verification of correct operation. Refrigerant and electrical connections are made for this purpose and there is a full charge of refrigerant in the system.
There is enough refrigerant to run the system on the pallet shown with no bubbles in the sight glass at 42F; more refrigerant will be required to fill lines in an installed system.
This is a good MRI/industrial chiller ready to work. No power cord or manual(s) included. No manuals, cords/cables, or additional items are included if not listed or shown.
- Manufacturer: Legacy
- Model: EST60S2-T4-Z
- Date of manufacture: 2007
- Minimum circuit ampacity: 30A/480V three phase
- Water connection: 1" FPT
- Controller: PSG
- Refrigerant: R-22
- System pump: 1.5hp centrifugal
- Compressor: 6hp scroll
- Temperature range: 42F - ambient without glycol; lower temperature is possible with glycol.
30 Day Guarantee
- Guaranteed to be as described
- Can be returned for flaws or malfunctions that were not disclosed
- See complete terms